#jsDisabledContent { display:none; } My Account | Register | Help
 Flag as Inappropriate This article will be permanently flagged as inappropriate and made unaccessible to everyone. Are you certain this article is inappropriate?          Excessive Violence          Sexual Content          Political / Social Email this Article Email Address:

# Vector group

Article Id: WHEBN0002711505
Reproduction Date:

 Title: Vector group Author: World Heritage Encyclopedia Language: English Subject: Collection: Transformers (Electrical) Publisher: World Heritage Encyclopedia Publication Date:

### Vector group

In electrical engineering, a vector group is the International Electrotechnical Commission (IEC) method of categorizing the high voltage (HV) windings and low voltage (LV) winding configurations of three-phase transformers. The vector group designation indicates the windings configurations and the difference in phase angle between them. For example, a wye HV winding and delta LV winding with a 30-degree lead is denoted as Yd11.

The phase windings of a polyphase transformer can be connected internally in different configurations, depending on what characteristics are needed from the transformer. In a three-phase power system, it may be necessary to connect a three-wire system to a four-wire system, or vice versa. Because of this, transformers are manufactured with a variety of winding configurations to meet these requirements.

Different combinations of winding connections will result in different phase angles between the voltages on the windings. Transformers connected in parallel must have the same vector group; mismatching phase angles will result in circulating current and other system disturbances.

## Contents

• Symbol designation 1
• Phase displacement 2
• See also 3
• References 4

## Symbol designation

The vector group provides a simple way of indicating how the internal connections of a transformer are arranged. In the system adopted by the IEC, the vector group is indicated by a code consisting of two or three letters, followed by one or two numeric digits. The letters indicate the winding configuration as follows:

• D or d: Delta winding, also called a mesh winding. Each phase terminal connects to two windings, so the windings form a triangular configuration with the terminals on the points of the triangle.
• Y or y: Wye winding, (also called a star). Each phase terminal connects to one end of a winding, and the other end of each winding connects to a common central point, so that the configuration resembles the letter Y. The central point may be connected outside of the transformer to a system neutral.
• Z or z: Zigzag winding, or interconnected star winding. Similar to a wye winding, but two windings form each phase are arranged so that the three legs are "bent" when the phase diagram is drawn. Zigzag-wound transformers have special characteristics and are not commonly used where these characteristics are not needed.
• III or iii: Independent windings. The three windings are not interconnected inside the transformer, and must be connected externally.
• N (uppercase): indicates that a system neutral is connected to the high-voltage side.
• n (lowercase): indicates that a system neutral is connected to the low-voltage side.

In the IEC vector group code, each letter stands for one set of windings. The high-voltage (HV) winding is designated with an uppercase letter, followed by medium or low-voltage (LV) windings designated with a lowercase letter. The digits following the letter codes indicate the difference in phase angle between the windings, with HV winding is taken as a reference. The number is in units of 30 degrees. For example, a transformer with a vector group of Dy1 has a delta-connected HV winding and a wye-connected LV winding. The phase angle of the LV winding lags the HV by 30 degrees.

Note that the high-voltage (HV) side always comes before the low-voltage (LV) side, regardless of which is the primary winding. This means that the vector group symbol will always start with a capital letter.

## Phase displacement

Phase rotation is always counterclockwise (internationally adopted convention) and indicates multiples of 30 degree lag for low voltage winding using the high voltage winding as the reference.

Thus 1 = 30°, 2 = 60°, 3 = 90°, 6 = 180° and 12 = 0° or 360°.

As the IEC60076-1 standard has stated, the notation is HV-LV in sequence. For example, a step-up transformer with a delta-connected secondary, and wye-connected primary, is written as 'Dy1'. The 1 indicates the LV winding lags the HV by 30 degrees.[1]

Transformers built to ANSI standards usually do not have the vector group shown on their nameplate and instead a vector diagram is given to show the relationship between the primary and other windings.

Removing harmonics: Dy connection – y winding nullifies 3rd harmonics, preventing it to be reflected on delta side.

Parallel operations: All the transformers should have same vector group & polarity of the winding.

Ground fault Relay: A Dd transformer does not have neutral. to restrict the ground faults in such systems, we may use a zigzag wound transformer to create a neutral along with the ground fault relay.

There is no technical difference between the one vector groups (i.e. Yd1) or another vector group (i.e. Yd11) in terms of performance. The only factor affecting the choice between one or the other is system phasing, i.e. whether parts of the network fed from the transformer need to operate in parallel with another source. It also matters if you have an auxiliary transformer connected to generator terminals.

## References

1. ^ IEC 60076-1 ed3.0
1. http://electrical-engineering-portal.com/understanding-vector-group-transformer-1
This article was sourced from Creative Commons Attribution-ShareAlike License; additional terms may apply. World Heritage Encyclopedia content is assembled from numerous content providers, Open Access Publishing, and in compliance with The Fair Access to Science and Technology Research Act (FASTR), Wikimedia Foundation, Inc., Public Library of Science, The Encyclopedia of Life, Open Book Publishers (OBP), PubMed, U.S. National Library of Medicine, National Center for Biotechnology Information, U.S. National Library of Medicine, National Institutes of Health (NIH), U.S. Department of Health & Human Services, and USA.gov, which sources content from all federal, state, local, tribal, and territorial government publication portals (.gov, .mil, .edu). Funding for USA.gov and content contributors is made possible from the U.S. Congress, E-Government Act of 2002.

Crowd sourced content that is contributed to World Heritage Encyclopedia is peer reviewed and edited by our editorial staff to ensure quality scholarly research articles.

By using this site, you agree to the Terms of Use and Privacy Policy. World Heritage Encyclopedia™ is a registered trademark of the World Public Library Association, a non-profit organization.

Copyright © World Library Foundation. All rights reserved. eBooks from World eBook Library are sponsored by the World Library Foundation,
a 501c(4) Member's Support Non-Profit Organization, and is NOT affiliated with any governmental agency or department.